Téléchargez votre mode d'emploi ou notice climatiseur TOSHIBA RAV-SP564ATZ-E
Le mode d'emploi climatiseur TOSHIBA RAV-SP564ATZ-E vous rend service
Téléchargez votre notice ! Téléchargement gratuit et sans inscription de tous types de documents pour mieux utiliser votre climatiseur TOSHIBA RAV-SP564ATZ-E : mode d'emploi, notice d'utilisation, manuel d'instruction.
Cliquez sur le bouton orange pour lancer le téléchargement du mode d'emploi TOSHIBA RAV-SP564ATZ-E - INSTALLATION MANUAL. La notice TOSHIBA est en Français.
Le téléchargement peut durer plus d'une minute, la notice fait 529 Ko.
Vous pouvez télécharger les notices suivantes connexes à ce produit :
TOSHIBA RAV-SP564ATZ-E DATA BOOK (1640 ko)
Extrait du mode d'emploi : notice TOSHIBA RAV-SP564ATZ-E
Les instructions détaillées pour l'utilisation figurent dans le Guide de l'utilisateur.
Wear heavy gloves during the installation work to avoid injury. ·
To Disconnect the Appliance from the Main Power Supply · This appliance must be connected to the main power supply by means of a switch with a contact separation of at least 3 mm. · A 16 A installation fuse (all fuse types can be used) must be used for the power supply line of this conditioner. 3
INSTALLATION OF NEW REFRIGERANT AIR CONDITIONER
New Refrigerant Air Conditioner Installation · THIS AIR CONDITIONER ADOPTS THE NEW HFC REFRIGERANT (R410A) WHICH DOES NOT DESTROY OZONE LAYER. R410A refrigerant is apt to be affected by impurities such as water, oxidizing membrane, and oils because the working pressure of R410A refrigerant is approx. 6 times as that of refrigerant R22. Accompanied with the adoption of the new refrigerant, the refrigerant oil has also been changed. Therefore, during installation work, be sure that water, dust, former refrigerant, or refrigerant oil does not enter the new type refrigerant R410A air conditioner circuit. To prevent mixing of refrigerant or refrigerant oil, the sizes of connecting sections of charging port on main unit and installation tools are different from those of the conventional refrigerant units. Accordingly, special tools are required for the new refrigerant (R410A) units. For connecting pipes, use new and clean piping materials with high pressure fittings made for R410A only, so that water and/or dust does not enter. 4
Super Digital Inverter
Required Tools/Equipment and Precautions for Use
Prepare the tools and equipment listed in the following table before starting the installation work. Newly prepared tools and equipment must be used exclusively. Legend
: Prepared newly (Use for R410A only. Do not use for refrigerant R22 or R407C etc. [...] If refrigerant gas leaks into the room and flows near a fire source, such as a cooking range, noxious gas may be generated. Electrical work must be performed by a qualified electrician in accordance with the Installation Manual. Make sure the air conditioner uses an exclusive power supply. An insufficient power supply capacity or inappropriate installation may cause fire. Use only the specified wiring during the unit installation. Ensure that all terminals are securely fixed, so preventing any external forces having a negative effect on the terminals. When the air conditioner cannot cool or heat a room well, contact the dealer from whom you purchased the air conditioner as refrigerant leakage is considered as the cause. In the case of repair that requires refill of refrigerant, ask service personnel about details of the repair. The refrigerant used in the air conditioner is harmless. Generally, the refrigerant does not leak. However, if the refrigerant leaks in a room and a heater or stove burner in the room catches fire, it may generate toxic gas. When you ask service personnel for repairing refrigerant leakage, confirm that the leakage portion has been completely repaired. Conform to the regulations of the local electric company when wiring the power supply. Inappropriate grounding may cause electric shock. ·
· · ·
· · · · ·
Super Digital Inverter
Do not install the air conditioner in a location that may be subjected to a risk of exposure to a combustible gas. If a combustible gas leaks and becomes concentrated around the unit, a fire may occur. Install the refrigerant pipe securely during the installation work before operating the air conditioner. If the compressor is operated with the valve open and without the refrigerant pipe, the compressor sucks air and the refrigeration cycle is overpressurized, which may cause a burst or injury. When carrying out the pump-down work, shut down the compressor before disconnecting the refrigerant pipe. Disconnecting the refrigerant pipe with the service valve left open and with the compressor still operating will cause air, etc. to be sucked in, raising the pressure inside the refrigeration cycle to an abnormally high level, and possibly resulting in rupturing, injury, etc. CAUTION
· Do not climb onto or place objects on top of the outdoor unit. [...]..